Magnetic Field of 1200kv Transmission Line by FEM & MATLAB
Akibahemad Arora1, Anuradha Deshpande2
1Mrs. Anuradha Deshpande*, Associate Professor, Department of Electrical Engineering, The M.S. University of Baroda, Vadodara, India.
2Mr. Akibahemad Arora, PG Student, Department of Electrical Engineering, The M.S. University of Baroda, Vadodara, India.
Manuscript received on September 26, 2019. | Revised Manuscript received on October 15, 2019. | Manuscript published on October 30, 2019. | PP: 1105-1110 | Volume-9 Issue-1, October 2019 | Retrieval Number: A9493109119/2019©BEIESP | DOI: 10.35940/ijeat.A9493.109119
Open Access | Ethics and Policies | Cite | Mendeley
© The Authors. Blue Eyes Intelligence Engineering and Sciences Publication (BEIESP). This is an open access article under the CC BY-NC-ND license (http://creativecommons.org/licenses/by-nc-nd/4.0/)
Abstract: With rapid industrial and commercial growth and flourishing population, power demand is increasing rapidly. Modern methods of UHV transmission lines are important to transmit bulk amount of power more efficiently in comparison to earlier methods of transmission. 1200 KV UHV transmission line is India future and therefore forthcoming project to tackle this situation. However as line to line voltage level increases, complexity of the transmission line increases. But, with higher level of line to line voltage, complexity of transmission line increases. ROW is one of the major concerns with transmission lines. Many parameters need to take care in designing; one of them is a magnetic field distribution at surroundings of transmission line. India has initiated to expand its UHV range to 1200kv. Paper suggest magnetic field of three configurations of the 1200KV line. Horizontal and vertical configuration test lines have been installed. Analysis has been done by two methods finite element method and (Method of images) analytical method. FEM is used to solve partial differential equations. Results from both methods have been compared. 3D electric field analysis of configuration also performed. Plotted results are compared with ICNIRP standards and safety limits defined. Adverse effects of excess magnetic field is also discussed. Biological effects of electromagnetic field on people, animals and plants are also discussed. Thus paper aimed at magnetic field calculation and verification with respect to standard. It also helps to utilize less right of way. The subject is under broad development due to its advantages over lower voltage levels and holds significance in future as well.
Keywords: Analytical Method, Finite Element Method (FEM), International commission on non-ionizing radiation protection (ICNIRP). Magnetic field, Right Of Way (ROW).